Spill containment testing is required every 3 years on regulated UST’s. Accurate will perform hydrostatic tests on the spill buckets, piping sumps and dispenser pans as required.
Our Consultant(s) provide services in a manner exhibiting the highest professional standards of skill, care, judgment and detail required by your project while keeping in compliance with all applicable codes and regulations having jurisdiction over the Project.
Accurate Tank Testing will provide the services of a New Jersey Department of Environmental Protection (NJDEP) Underground Storage Tank (UST) Class A/B Operator to manage the UST facility inspection and testing program required to fulfill the duties a Trained Class A/B Operator as described in the NJDEP Storage of Hazardous Substances Rule, N.J.A.C. 7:14B (UST…
A/L Testing applies to Vapor Assist dispensing facilities only. This test is required on an annual basis and will be conducted in accordance to TP-201.5. The volume of the air mixture is recorded and compared with the volume of the gasoline dispensed from each nozzle.
A tie-tank test is required on an annual basis and will be conducted in accordance with CARB test procedure TP-201.3C to determine the vapor piping connections between the tanks. Tie-Tank testing is included in the pressure decay price.
Blockage Testing is required tri-annually on all gasoline UST’s to confirm proper function of vapor recovery.
P/V Valve testing is required on an annual basis and will be conducted in accordance to CARB test procedure TP-201.1E. Positive and negative pressure leak rates and cracking pressures will be measured. Failing P/V valves will be replaced with new tested P/V valves.
Pressure Decay testing (Stage I or Stage II Vapor Recovery Testing) is required on an annual basis and will be conducted in accordance to California Air Resources Board (CARB) test procedure TP-201.3. All tank piping and dispenser accesses will be opened. All obvious worn or broken accessible tank/dispenser fittings will be replaced as needed. Pressure…
UST’s and/or piping protected by sacrificial anodes (ex. Stip-3’s) and/or impressed current systems must be tested within 6 months of installation and every 3 years thereafter. Accurate will perform the required CP testing per N.J.A.C. 7:14B-5.2..
Annual line testing is required on all single wall product piping, unless electronic leak detectors are installed and functioning properly.